PART IGeneral Requirements
3 For the purpose of ensuring the safety of an installation, no operator shall use the installation unless the equipment on the installation is arranged in accordance with these Regulations to
(a) provide for the safety of personnel;
(b) minimize damage to the environment; and
(c) enable easy access to the equipment.
4 (1) Every new installation shall be designed, constructed, installed and commissioned in accordance with a quality assurance program that complies with subsection (2) and that is selected in accordance with Canadian Standards Association CAN3-Z299.0-86, Guide for Selecting and Implementing the CAN3-Z299-85 Quality Assurance Program Standards.
(2) A quality assurance program shall be developed in accordance with
(a) Canadian Standards Association CAN3-Z299.l-85, Quality Assurance Program — Category 1;
(b) Canadian Standards Association CAN3-Z299.2-85, Quality Control Program — Category 2;
(c) Canadian Standards Association CAN3-Z299.3-85, Quality Verification Program — Category 3; and
(d) Canadian Standards Association CAN3-Z299.4-85, Inspection Program — Category 4.
(a) conform to Transport Canada TP 4414, Guidelines Respecting Helicopter Facilities on Ships; and
(b) be equipped so that any fuel stored on or adjacent to the helicopter deck or to the accommodation areas
(2) Every helicopter deck that forms part of an installation shall be in a location that is readily accessible to and from the dependent personnel accommodation of the installation.
Facilities for Inspection and Maintenance
6 An installation shall be designed and equipped in such a manner as to allow for the monitoring, maintenance and periodic inspection of the installation, including
(a) clear marking and identification of the areas to be inspected;
(b) provision for safe access to and adequate inspection space for the areas to be inspected;
(c) space for the storage and operation of diving equipment;
(d) means to facilitate the work of divers, where inspection by divers is required;
(e) means to assist maintenance personnel, including those doing underwater maintenance, to perform their work safely and effectively; and
(f) in the case of a mobile platform that is not intended to be periodically drydocked, means to facilitate on-location inspection of the hull.
Secondary Structures and Fittings
7 All decks, deckhouses, skids, modules and other structures located or installed on an installation shall be capable of withstanding all the loads and forces to which they will be subjected, as determined in accordance with section 44.
Arrangements of Materials and Equipment
- flame-type equipment
flame-type equipment means any electric or fired heating equipment that uses an open flame, electric arc or element, and includes a space heater, a torch, a heated process vessel, a boiler, an electric arc or an open flame welder, or an open element electric heater or appliance; (équipement de type à flamme)
- process vessel
process vessel means a heater, dehydrator, separator, treater or vessel used in the processing or treatment of produced gas or oil. (récipient de fabrication)
(2) No person shall create or cause to be created any unprotected flame or source of ignition within 50 m of a well, an oil storage tank or other source of ignitable vapour.
(3) No flame-type equipment shall be placed or operated within 25 m of a well, an oil storage tank or other source of ignitable vapour, except
(a) where the well is
(b) where emergency works requires the use of flame-type equipment and the wellhead valves and blow-out preventer, if any, are closed.
(4) No flame-type equipment shall be placed or operated within 25 m of a process vessel, unless the flame-type equipment is fitted with an adequate flame arrester.
(5) No flame-type equipment shall be located in the same building as a process vessel or other source of ignitable vapour, unless
(6) All process vessels and equipment from which ignitable vapour may issue shall be vented to the atmosphere, and all vent lines from every storage tank that is vented to flare pits or flare stacks shall be provided with flame arresters or other equivalent safety devices.
(7) An exhaust pipe from an internal combustion engine located within 25 m of a well, a process vessel, an oil storage tank or other source of ignitable vapour shall be constructed so that
(8) All equipment at or near a well, a process vessel, an oil storage tank or other source of ignitable vapour shall be constructed in accordance with Part I of the Canadian Electrical Code Part I and the Oil and Gas Occupational Health and Safety Regulations.
Access to Hazardous Areas
(2) Subject to subsections (3) to (5), an enclosed area that has direct access to, and that is classified as less hazardous than, a Class I, Division 1, hazardous area or a Class I, Division 2, hazardous area shall be considered to have the same classification as the area to which it has direct access.
(3) An enclosed area that has direct access to a Class I, Division 1, area shall be considered to be a Class I, Division 2, hazardous area if
(4) An enclosed area shall not be considered to be a hazardous area because of its direct access to a Class I, Division 2, hazardous area if
(5) An enclosed area shall not be considered to be a hazardous area because of its direct access to a Class I, Division 1, hazardous area if
(6) Piping systems on an installation shall be designed to preclude direct communications between hazardous areas of different classifications and between hazardous and non-hazardous areas.
- Date modified: