PART IVUnloading Operations (continued)
38 Tank cars shall not be unloaded after sundown unless the unloading rack, tank car dome and other areas of activity on the unloading site are adequately lighted by permanent flood lights, installed and otherwise in conformity with the provisions of the Canadian Electrical Code, Part I, Eighth Edition and amendments thereto, or in accordance with any other higher standard prescribed by the local authority. Any electrical facilities within 20 feet of the unloading rack or tank car connection shall be suitable for a corrosive atmosphere.
39 At least one 20 pound ABC, dry chemical fire extinguisher or its equivalent shall be located at the unloading site and be readily available to the unloading operator during unloading operations.
40 (1) At least one respirator of the self-contained type and approved for use in chlorine atmospheres by the United States Bureau of Mines, together with a person trained in its use, shall be available on the site on not more than 20 minutes notice.
(2) At least two respirators of the absorbing canister type and approved for use in chlorine atmospheres by the United States Bureau of Mines, together with a person trained in their use, shall be readily available on the site during unloading operations.
41 (1) A chlorine emergency repair kit of a type recommended by The Chlorine Institute for the repair of tank cars, together with a man qualified to use it, shall be available on the site on short notice.
(2) Instruction cards, which provide information essential to the emergency handling of chlorine leaks, such as the location of respirators and the phone numbers listed hereunder, shall be posted in a conspicuous place outside near the unloading rack or inside near the unloading site telephone:
(a) the phone number of at least one senior officer of the company owning or operating the unloading facility;
(b) the phone numbers of the nearest police department, fire department and hospital;
(c) the phone numbers of the principal public and institutional buildings within 2,000 feet of the unloading rack;
(d) the phone number of at least one person who is available on short notice and is competent in handling chlorine leaks and similar emergencies;
(e) the phone numbers of at least two persons who are available on short notice and are competent in the use of chlorine emergency repair kits; and
(f) the phone number of the nearest agent or officer of the railway company serving the facility.
(3) The owning or operating company shall have at least one person available on short notice during unloading operations who has been trained in the handling of major chlorine leaks and other similar emergencies and that person shall participate in periodic safety drills, which shall include practice in the proper use of respirators, and other safety equipment.
42 The deliberate venting of chlorine to the atmosphere in quantities sufficient to cause injury to a person on the unloading site or in quantities sufficient to escape the boundaries of the unloading site is prohibited.
43 A weatherproof sign measuring not less than 12 inches by 12 inches and bearing the word “CHLORINE” in black letters at least four inches high on a yellow background shall be attached in a conspicuous place to the unloading rack or to a post near the rack.
44 The exterior of the piping system shall be painted or otherwise protected from atmospheric corrosion.
(2) Leaking or defective pipes, fittings, valves or other parts of the unloading system shall be repaired or replaced by a qualified person and this work shall be undertaken immediately or with the minimum of delay that is consistent with good safety practice. That portion of the system to be repaired or replaced shall be isolated from the rest of the system and purged of chlorine in a manner that will not violate section 42.
(2) No combustible or other dangerous commodity, except chlorine, shall be stored or handled on the unloading site unless that commodity is mentioned in the approved application or is otherwise sanctioned by the approving order.
47 All chlorine unloading facilities subject to these Regulations may be inspected at any time by an officer of the Commission.
48 The owning or operating company shall report immediately by wire to the railway company concerned and to the Director of Operation, Canadian Transport Commission, Ottawa, Ontario, every fire, explosion, pipeline rupture, or any occurrence that results in the accidental release of chlorine from the system in quantities sufficient to escape the boundaries of the unloading site or causes injury to a person on the site to the extent that medical attention is required.
49 Violations of any provision of these Regulations are subject to such penalty as may be provided in the Railway Act.
50 The principal hazards associated with the unloading of tank cars of chlorine are discussed in Schedule IV.
- Date modified: