PART 2Energy-Using Products (continued)
DIVISION 5Boilers (continued)
SUBDIVISION BOil-Fired Boilers (continued)
322 For the purpose of subsection 5(1) of the Act, the information set out in column 3 of the table to this section must be collected in accordance with the standard set out in column 2 and provided to the Minister in respect of an oil-fired boiler described in column 1.
|Column 1||Column 2||Column 3|
|1||Household oil-fired boilers manufactured on or after December 31, 1998 and before September 1, 2010||CSA B212|
|2||Household oil-fired boilers manufactured on or after September 1, 2010 and before January 15, 2021||ASHRAE 103 for information set out in paragraphs (a) to (f)|
|3||Household oil-fired boilers manufactured on or after January 15, 2021||CSA P.2 for information set out in paragraphs (a) to (e)|
|4||Commercial oil-fired boilers manufactured on or after January 1, 2025||10 C.F.R. Appendix A|
- SOR/2019-164, s. 23
SUBDIVISION CElectric Boilers
Marginal note:Definition of electric boiler
323 In this Subdivision, electric boiler means a boiler that uses electric energy as a source of heat, is intended for application in a hot water central heating system, has an input rate of less than 88 kW (300,000 Btu/h) and is not equipped with tankless domestic water heating coils.
Marginal note:Energy-using product
(2) However, for the purposes of sections 4, 5 and 325, an electric boiler is not considered to be an energy-using product unless it is manufactured on or after September 1, 2012.
Marginal note:Energy efficiency standard
325 The energy efficiency standard that applies to an electric boiler is that it must be equipped with an automatic water temperature adjustment device without which the boiler is not operable.
326 For the purpose of subsection 5(1) of the Act, the following information must be provided to the Minister in respect of an electric boiler:
(a) its input rate, expressed in kilowatts, collected in accordance with ASHRAE 103; and
(b) the type of automatic water temperature adjustment device that it has.
[327 to 368 reserved]
DIVISION 6Water Heaters
369 The following definitions apply in this Division.
- CSA P.3-15
CSA P.3-15 means the CSA standard CAN/CSA-P.3-15 entitled Testing method for measuring energy consumption and determining efficiencies of gas-fired and fuel oil-fired water heaters. (CSA P.3-15)
- first-hour rating
first-hour rating means, in respect of a gas-fired storage water heater or an oil-fired water heater, the measure of the maximum volume of hot water that the water heater can supply within an hour that begins when the water in the water heater is fully heated. (capacité de première heure)
- 10 C.F.R. Appendix A
10 C.F.R. Appendix A means Appendix A to Subpart G, Part 431 of Title 10 to the United States Code of Federal Regulations, entitled Uniform Test Method for the Measurement of Thermal Efficiency and Standby Loss of Gas-Fired and Oil-Fired Storage Water Heaters and Storage-Type Instantaneous Water Heaters, as amended from time to time. (appendice A 10 C.F.R.)
Vr means the nominal volume, expressed in litres, of a water heater’s storage tank. (Vr)
Vs means the measured storage volume, expressed in litres, of a water heater’s storage tank. (Vs)
- SOR/2018-201, s. 38
- SOR/2019-164, s. 24
SUBDIVISION AElectric Water Heaters
370 The following definitions apply in this Subdivision.
- bottom inlet
bottom inlet means a cold water inlet, other than one with a dip tube, that enters near the bottom of the water heater’s storage tank. (entrée inférieure)
- CSA C191-04
CSA C191-04 means the CSA standard CAN/CSA-C191-04 entitled Performance of Electric Storage Tank Water Heaters for Domestic Hot Water Service. (CSA C191-04)
- electric water heater
electric water heater means a stationary electric storage tank water heater that is intended for use on a pressurized water system and that has a Vr of at least 50 L (13.21 US gallons). (chauffe-eau électrique)
- 10 C.F.R. Appendix B
10 C.F.R. Appendix B means Appendix B to Subpart G, Part 431 of Title 10 to the United States Code of Federal Regulations, entitled Uniform Test Method for the Measurement of Standby Loss of Electric Storage Water Heaters and Storage-Type Instantaneous Water Heaters, as amended from time to time. (appendice B 10 C.F.R.)
- SOR/2018-201, s. 39
- SOR/2019-164, s. 25
370.1 For the purpose of these Regulations, an electric water heater is one of the following types:
(a) household, if it has an input rate of less than 12 kW (40,982 Btu/h); or
(b) commercial, if it is has an input rate of greater than or equal to 12 kW (40,982 Btu/h).
- SOR/2019-164, s. 26
- Date modified: