PART 14Confined Spaces (continued)
- SOR/2019-246, s. 294(F)
(2) If an airborne hazardous substance or oxygen in the atmosphere in a confined space is maintained at the value, level or percentage referred to in subsection 171(2) by the use of ventilation equipment, a person may only be granted access to the confined space if
(a) the ventilation equipment is
(b) in the event of failure of the ventilation equipment, sufficient time will be available for the person to escape from the confined space before one of the following occurs:
(3) The employee referred to in subparagraph (2)(a)(ii) must activate an alarm in the event of faulty operation of the ventilation equipment.
- SOR/2019-246, s. 295
PART 15Electrical Safety
175 The following definitions apply in this Part.
- control device
control device means a device that will safely disconnect electrical equipment from its source of energy. (dispositif de commande)
- direct supervision
direct supervision means on-site, in-view observation and guidance by a qualified person while an employee performs an assigned task. (supervision immédiate)
guarantor means a person who gives a guarantee of isolation. (garant)
guarded means in respect of electrical equipment, covered, shielded, fenced, enclosed or otherwise protected by means of suitable covers or casing, barriers, guardrails, screens, mats or platforms to remove the possibility of dangerous contact or approach by persons or objects. (protégé)
- person in charge
person in charge means a qualified person who supervises employees performing work on or a live test of isolated electrical equipment. (responsable)
(2) Before authorizing a person to test or perform work on electrical equipment, the employer must ensure that a work permit referred to in section 166 has been obtained.
(3) If there is a risk that the person in charge or the employee under the direct supervision of the person in charge could receive a hazardous electrical shock during the performance of their testing or work,
(4) Subject to subsection (5), if an employee is working on or near electrical equipment that is live or may become live, the electrical equipment must be guarded.
(5) If it is not feasible for the electrical equipment to be guarded, the employer must take measures to protect the employee from injury by insulating the equipment from the employee or the employee from the ground.
- SOR/2019-246, s. 296
177 (1) If an employee is working on or near live electrical equipment and, because of the nature of the work or the condition or location of the work place, it is necessary for the safety of the employee that the work be observed by a person not engaged in the work, the employer must appoint a safety watcher
(2) Safety watchers must be
(a) informed of their duties as safety watchers and of the hazard involved in the work;
(b) trained and instructed in the procedures to follow in the event of an emergency;
(c) authorized to stop immediately any part of the work that they consider dangerous; and
(d) free of any other duties that might interfere with their duties as safety watchers.
(3) For the purposes of subsection (1), employers may appoint themselves as safety watchers.
- SOR/2019-246, s. 297(F)
Coordination of Work
178 If an employee is working on or in connection with electrical equipment, that employee and every other person who is so working, including every safety watcher, must be fully informed by the employer with respect to the safe coordination of their work.
Switches and Control Devices
(2) The path of access to every electrical switch, control device or meter must be free from obstruction.
(3) If an electrical switch or other control device controlling the supply of electrical energy to electrical equipment is operated only by a person authorized to do so by the employer, the switch or control device must be fitted with a locking device that only the authorized person can activate.
(4) Control switches for all electrically operated machinery must be clearly marked to indicate the switch positions.
Defective Electrical Equipment
180 Defective electrical equipment must be disconnected from its power source by a means other than the control switch and notices must be placed on the equipment and at the control switch to indicate that the equipment is defective.
(2) An employee must not replace missing or burnt-out fuses unless authorized to do so by a person in charge.
Power Supply Cables
(2) A three-wire power supply cable on electrical equipment or appliances must not be altered or changed for the purpose of connecting the equipment or appliances to a two-wire power supply.
- SOR/2019-246, s. 298(E)
Grounded Electrical Equipment
183 Grounded electrical equipment and appliances must be used only when connected to a matching grounded electrical outlet receptacle.
Additional Requirement for the Issuance of a Work Permit
184 In addition to the requirements set out in section 168, before an employer issues a work permit for electrical equipment under section 166, the employer must provide a guarantee of isolation in respect of each source of electrical energy.
Guarantees of Isolation of Electrical Equipment
(2) No more than one employee is to give a guarantee of isolation for a piece of electrical equipment for a given period.
(3) Before an employer issues a work permit, the person in charge must receive from the guarantor
(4) The written guarantee of isolation referred to in paragraph (3)(a) must be signed by the guarantor and by the person in charge and must contain the following information:
(a) the date and hour when the guarantee of isolation is given to the person in charge;
(b) the date and hour when the electrical equipment will become isolated;
(c) the date and hour when the isolation will be terminated, if known;
(d) the procedures by which isolation is assured;
(e) the name of the guarantor and the person in charge; and
(f) a statement as to whether live tests are to be performed.
(5) If a non-written guarantee of isolation referred to in paragraph (3)(b) is given, a written record of the guarantee must, as soon as feasible, be made by the guarantor and signed by the person in charge.
(6) A written record must contain the information referred to in subsection (4).
(7) Every written guarantee of isolation and every written record must be
(a) kept by the person in charge and made readily available for examination by the employee performing the work or live test until the work or live test is completed;
(b) given to the employer when the work or live test is completed; and
(c) kept by the employer for a period of one year after the completion of the work or live test at his place of business nearest to the work place in which the electrical equipment is located.
(8) If a written guarantee of isolation or a written record of an oral guarantee of isolation is given to a person in charge and the person in charge is replaced at the work place by another person in charge before the guarantee has terminated, the other person in charge must sign the written guarantee of isolation or written record of the oral guarantee of isolation.
(9) Before an employee gives a guarantee of isolation for electrical equipment that obtains all or any portion of its electrical energy from a source that is not under the employee’s direct control, the employee must obtain a guarantee of isolation in respect of the source from the person who is in direct control of the source and is authorized to give the guarantee in respect of that source.
- SOR/2019-246, s. 299
- Date modified: